Commercial and Industrial water ionizers EHM-3000 Specification:
Working Mode: Continuous
Rated Voltage: 220V, 50Hz
Rated Power: 3,000W
Source Water: The source water can meet the standard of our country and the rigidity is less than 100mg/L and the water pressure is between 0.1 and 0.25Mpar. The rigidity of municipal water is less than 100m according with national standards and the water pressure is more than 0.3Mpar. Environment temperature can be from 5 to 40°C and the humidity is less than 80%.
The PH value of the Alkalescent Water is between 7.0 and 10.0, it is more than 3000L/h.
Useful life of electrolyzed slot is more than 2500h and the dimension is L75*W250*H120cm.
The net weight is 350KG including the following fittings: 2 switches, 1 fuse, instructions for orp, ph, conductivity, several plastic parts and a lock which is for the back door ( to avoid the shipping damage, we will not install it)
Part B is the facade of the pre-filtering system. ① conductivity probe, ②filter-pressure meter, ③precision filter, ④⑤⑥is the C1, C2, C3’s inlet water valve to the electrolysis chamber.
Part C is the facade of the electrolysis chamber.①is the meter of acid water outlet of the first electrolysis chamber. ②is the meter of alkaline water outlet of the first electrolysis chamber, ③ is the is the meter of acid water outlet of the second electrolysis chamber, ④ is the is the meter of alkaline water outlet of the second electrolysis chamber, ⑤is the meter of acid water outlet of the third electrolysis chamber, ⑥is the meter of alkaline water outlet of the first electrolysis chamber;⑦,⑧,⑨,⑩,⑾,are the valves corresponding to the ①,②,③,④,⑤,⑥.
is the facade of the Electric Control System(ECS), ①ammeter②Power indicator③voltmeter④PH&ORP⑤Knob to enhance voltage⑥conductivity meter⑦indicator light point A⑧AB switch⑨Indicator light point B⑩Working indicator ⑾ is “start” button to start the system.⑿ is the “stop” button to stop the system. ⒀is the pump indicator light, ⒁ is the“ start” button to the pump ⒂ is the“ stop ”button to the pump.
Part E: ECS structure
Part E: Inside of the electric control system. ①Air Switch ②fuse③Joint of the water level Signal④Power supply for the Pump⑤Power cord
Part A: Profile of the system
Part A: water –input profile.① Acid water output ②waste water output
③Valve of waste water④Alkaline water out put ⑤ tap water input ⑥ PH/ORP Tester
⑦Pressure -discharge ⑧ Magnetic valve for pressure discharge ⑨Air- discharge valve for the filtering
Prepare the water tank and the pump.
Tap water input connection
Connect the water tank and the plum to the system.
A5 is the water inlet, which connects to the outlet of the pump.
A4 is the outlet of the alkaline water
A1 is the outlet of the acid water.
A2 is the outlet of the waster water.The alkaline water is not very good when the system works 5 mintutes initially each time, and pls turn on the A3 valve to discharge.
A7 is pressure –discharge valve.If the water pressure is too high for the electrosis chamber, the A8 will turn on auto-matically and the water will be discharged by A7 outlet.
This system includes the control system of the water tank and the water pump, so please prepare the water tank and the pump.
If your requirement of the alkaline water is not very high, you may not connect the A2 ( the waste water outlet); if you want to connect the A2 to the pipe, the height of the A4 pipe shall be higher than A2’s location, otherwise, the waste water can’t be discharged.
Electric control system connection.
E 1 is the power supply cord of the whole system.
E3 is the connection to the water level signal, connect the signal cord to the E3.The installation of the signal switch, please refer to the instructions.
E4 is the joint to the pump, please connect the pump cord to the E4.
Application for commercial water ionizer:
A. For restaurants, food plants use: improve the food taste, and keep the nutritions in the vagetables and meats.
B. For directly drinking: Keep body pH balance and avoid the sub-health and diseases. With the smaller molecule, the water is easily absorbed by the body.
C. For the farm use:
(1) can keep the cattles health, keep their furs shining, and improve the milk production.
(2) can control and offer prevention of fruits, vegetables and other plants from a variety of diseases, alternative chemical pesticides;
(3) could effectively degrade the surface of plant pesticide residues;
(4) could effectively kill the seeds carried by micro-organisms and fungi;
(5) can be suitably modified alkaline soil.
Water Storage conditions:
(1) water storage containers to be sealed;
(2) to avoid direct exposure to light;
(3) The storage ambient temperature is not greater than 40 Celsius;
Under these conditions, the alkaline & acidic electrolyzed oxidizing water could be stored for at least 90 days.
Safety Emissions: acidic electrolyzed oxidizing water in irrigation or placed after a certain time, be able to restore its own ordinary water, and plants were polluting the environment and residual.
Other Application for commercial water ionizer:
Poultry Farm for Healthier Birds, lower mortality of birds, better cleaning of the birds, and Eggs.
Hospitals: For Faster recovery of patients, better disinfection of O.T. and Treatment areas, better Hygiene of all areas
Hotels: Better cleaning of food stuff, better hygiene & sanitation in all areas , plus better health of the employees.
Agriculture: Better germination of seeds, healthier plants, NO USE of pesticides and chemicals required. Harvested Vegetables and Fruits and flowers> cleaned with alkaline water remain fresh for longer period.
Marine/ Meat Food Industry: Alakline water used for disinfecting and cleaning the fish & meat, removes bacteria & ecoli
1.Inspecting commercial water ionizer
Checking the voltage and the ground cord connecting is right or not.
Ensure the all related valves turn on.
Place the D5 (Volt. Adj. )at the lowest
Ensure the tap water can meet the following requirements:
The PH is not less than 6.3
The conductivity is between120us/cm to 30us/cm
Inlet water temperature: 5-40°C
Inlet water pressure: 0.1-0.25MPa
Power supply: 220V/ 50A
Ground cord is required, the resistance is 4Ω
2. How to Start commercial water ionizer
After inspection, please adjust the D5 as “0” and turn on the E1 ( air switch), the D2 will be light.
Press the “system start” button, the D11&D10 will be light.
Turn on the inlet water valve and the pump, the D14&D13 will be light.
Turn D8 to Point A, at the meaning while, please reserve the flow meter and the D1 Am meter, then please adjust the D5 voltage and the current can’t be over 150A. When the flow rate is up to 3000 liters per hour, plsese test the PH of the water, if it can meet the requirement, pls turn off the A2( the waste water –discharge valve). It turns out the system works properly.
3. How to Stop commercial water ionizer.
1) Turn on A2 and adjust the D5 as “0”,then make the D8 in the middle.
2) Press D15 turn off the pump，then D13 light will be off.
3) press D12 to stop the system, then D10light will be off
4) Turn off the E1
Please follow the instructions strictly before operation.
While the system works about 4 hours, pls turn on A2 and adjust the voltage as “0” and discharge the waste water, and then place the A8 to Point B and adjust the voltage to increase then turn off the A2.After the system woks 4 hours at point B, please turn to A as the same way, therefore 4 hours is a phase to point A &B.
4. Maintenance and Attention
Keep A-B working usually
Keep system clean
Inspect the system frequently
Froze protection needed
Clean the system when it not used for several days.
Non-working for long time,please use the non-Aircompressor to blow it.
Reserve the flow meter.
Can’t turn off the flow valve competely
Attention to the water press which can’t be over the working range.
Q: Alkaline and acid water inverts
A: pls plug the wires inverts.
Q: No variation to the vlotage
A: replace the Si PCB Board.
Q:The fuse offen burns
A: Replace the diode
Q:There is only one pipe having water for the discharge flow meter or the purified water flow meter
A:Replace the magnetic valve.
Q:PH is not good after rising the voltage
A: Replace the electrolysis chamber